Display: Dual 4 digits, red LED, -1999 to 9999
|DIN SIZE||PV Display|
|1/16||0.45 (11.3)||0.37 (9.5)||7.0 (198)|
|3/16||0.55 (14.0)||0.47 (12.0)||12.4 (352)|
|1/8 (V)||0.54 (13.6)||0.41 (10.5)||11.8 (333)|
|1/4||0.81 (20.5)||0.43 (11.0)||14.9 (421)|
Front Panel: Panel gasket provided. 1/16 & 1/8 DIN: IP65, 3/16 & 1/4 DIN: IP55
Programming Methods: Four front panel buttons and Modbus
Ramp & Soak Programs: 2 with 15 segments each
Noise Filter: Programmable 1 to 120 seconds or off
Display Update Rate: 4/second
Password: Restricts modification of programmed settings.
Non-Volatile Memory: Settings stored for a minimum of 10 years
Power: 100-240 VAC, 50/60 Hz, 10 W
Required Fuse: UL Recognized, 1 A, 250 V, slow-blow
Isolation: 2300 V input/output-to-power line; 4 kV relay output-to-input/output/power line.
Operating Temperature: 10 to 50°C
Storage Temperature: -40 to 85°C
Relative Humidity: 20 to 90% non-condensing
Enclosure: 1/16, 3/16, 1/8, & 1/4 DIN available; impact-resistant plastic; color: black
UL File Number: E244207; Process Control Equipment
Approvals: UL & C-UL Recognized, CE Compliant
Warranty: 3 years parts & labor
Inputs: Field selectable: 0.4 to 2.0 V, 1 to 5 V, 0 to 10 V, -10 to 20 mV, 0 to 100 mV. 4-20 mA input requires 100 Ω resistor connected across input terminals (order P/N: PDX-RES1).
Accuracy: ±0.1% FS ±1 count or 9999
Calibration: All inputs are calibrated at the factory
Scale Range: User programmable over entire range
Transmitter Supply: 14 to 18 VDC @ 20 mA; available at terminals OUT2 or OUT3, instead of retransmitting analog output; selection is made through the front panel
Ratings: 1 Form C (SPDT) standard; rated 3 A @ 30 VDC or 3 A @ 250 VAC resistive load. 1 or 2 Form A (SPST) optional; rated 1 A @ 30 VDC or 1 A @ 250 VAC resistive load.
Relay Operation: Time proportional PID control, forward or reverse (fail-safe) alarms, inner signal PV or SP zones, program segment time signals, or program run or end alerts
Cycle Time: 1 to 300 seconds; time proportional PID control only.
High/Low Alarm: User may program any alarm for absolute high or low trigger values.
Deviation Alarm: User may program any relay for high, low, or high/low range set point deviation alarm.
Alarm Deadband: 0-100% FS, user selectable
Alarm Delay: 0 to 99 minutes and 59 seconds
Reverse Operation (Fail-Safe): Programmable, independent for each alarm. Relay coils are energized in non-alarm condition. In case of power failure, relays will go to alarm state.
Forward Operation: Relay coils are energized in alarm condition. In case of power failure, relays will go to non-alarm state.
Inner Signal Zones (IS): Relay activates with inner signal 1 or 2 states, based on the value of the PV, SP, or target >SP of the program segment. Two programmable trigger value ranges.
Time Signal (TS): Relay activates during program segments with time signals.
Program Run (RUN): Relay activates during program operation.
Program End Alert (PEND): Relay activates for 15 seconds following reset at program completion.
Auto Alarm Initialization: Normal and standby operation independent for each alarm. Normal alarms will reflect the state of the input to the controller at all times. Standby alarms will not trigger if the change to alarm state is a result of power up cycle, set point change, or alarm configuration change.
Inputs: Factory calibrated, field selectable: J, K, T, E, B, R, S, L, U, N, W, and Platinel II thermocouples and 100 Ω platinum RTD (0.00385 or 0.00392 curve)
Cold Junction Reference: Automatic or off
Offset Adjustment: Four programmable input bias zones
Sensor Break: Up or down scale, user selectable; display reads S.OPN; alarm relays will follow the up or down scale selection.
|Type||Range (°C)||Range (°F)||Accuracy|
|K1||-200 to 1370||-300 to 2500||>0ºC: ±0.1% FS ±1 count|
<0ºC: ±0.2% FS ±1 count
|K2||-199.9 to 999.9||0 to 2300|
|J||-199.9 to 999.9||-300 to 2300|
|T||-199.9 to 400.0||-300 to 750|
|E||-199.9 to 999.9||-300 to 1800|
|B||0 to 1800||32 to 3300||>400ºC: ±0.15% FS ±1 count|
<400ºC: ±5% FS ±1 count
|R||0 to 1700||32 to 3100||±0.15% FS ±1 count|
|S||0 to 1700||32 to 3100|
|L||-199.9 to 900.0||-300 to 1600||>0ºC: ±0.1% FS ±1 count|
<0ºC: ±0.2% FS ±1 count
|U||-199.9 to 400.0||-300 to 750|
|N||-200 to 1300||-300 to 2400||>0ºC: ±0.1% FS ±1count|
<0ºC: ±0.25% FS ±1 count
|W||0 to 2300||32 to 4200||±0.2% FS ±1 count|
|Platinel II||0 to 1390||32 to 2500||±0.1% FS ±1 count|
|PtA||-199.9 to 850.0||-300 to 1560||±0.1% FS ±1 count|
|PtB||-199.9 to 500.0||-199.9 to 999.9|
|Ptc||-19.99 to 99.99||-4.0 to 212.0||±0.2% FS ±1 count|
|JPtA||-199.9 to 500.0||-199.9 to 999.9||±0.1% FS ±1 count|
|JPtB||-150.0 to 150.0||-199.9 to 300|
* Performance within recommended operating conditions (10 to 50 ºC, 20 to 90% RH)
Configuration: 2 or 4 open collector transistor
Operation Modes: Alarms, inner signal zones (IS), program segment time signals (TS), SP status (ramp up/down or soak), program running (RUN) or end alerts (PEND). See Relays above for operation mode details.
Transistor Rating: 24 VDC @ 50 mA
Scaling Range: Retransmitting 4-20 mA outputs can be scaled for any range.
Accuracy: ±0.1% FS
Availability:1/16 & 3/16 DIN: 1 standard, 1 optional, 1/8 & 1/4 DIN: 2 standard
Output Operation: 4-20 mA PID control, time proportional voltage pulse PID control, or 4-20 mA retransmitting
Ratings: Continuous 4-20 mA PID or retransmitting: 600Ω max. Time Proportional PID: 15 VDC pulse high, less than 0.1 VDC pulse low; 600 Ω minimum, current limited at 30 mA
Cycle Time: 1 to 300 seconds; time proportional PID control only
Power: Internally powered 4-20 mA output
Isolation: 500 V input-to-output
Output Loop Resistance: 600 Ω max
Configuration: Two contacts, two operating modes
Contacts: Normally open switches (external excitation not required) or open collector transistor
Open Circuit Voltage: Approximately 5 VDC
Logic Levels: LO = 0 to 0.8 VDC, HI = 4.7 to 28 VDC
Operation Modes: Mode 1: Program hold and step;
Mode 2: Program run or reset.
Protocol: PC, Modbus (ASCII, RTU), Sync (Master SP Control)
Address: 1 to 99 (Max 31 units connected)
Baud Rate: 600 to 19,200 bps
Data: 7 or 8 bit, automatic when using Modbus protocol
Transmit Time Delay: 0 to 100 ms
Stop Bit: 1 or 2
Parity: None, even, or odd